Maintenance and maintenance of emergency led lights for house
The emergency led lights for house is a sign that points out the escape route for the evacuation of people and when a fire occurs. It is composed of various emergency led lights for house and related devices. Fire emergency lamps refer to all types of lamps that provide lighting and signs for personnel evacuation and fire fighting operations, including fire emergency lighting lamps, fire emergency sign lamps and fire emergency lighting sign lamps. Emergency led lights for house refers to signs used to instruct people to evacuate safely in the event of a fire.
emergency led lights for house maintenance requirements
(1) It should be firm and unobstructed, and the emergency led lights for house should be in normal state.
(2) After the normal power supply is cut off, the duration of the emergency working state shall not be less than that specified in Table 3-15.
(3) The ground illuminance of emergency led lights for house should not be less than 0.5Ix, and the ground illuminance of underground engineering evacuation lighting should not be less than 5.0Ix.
(4) Power distribution room, fire control room, fire pump room, smoke-proof and smoke-exhausting machine room, battery room for fire-fighting power, self-provided generator room, telephone exchange room, and other rooms that still need to work in the event of a fire, and their work The illuminance of the surface should not be lower than the illuminance under normal lighting.
The owner of emergency led lights for house shall properly keep the required luminous signs. The owner should perform a visual inspection of signs and symbols at least once every 12 months with normal lighting on. Marks and markings that are missing, damaged, loose or showing worn or missing MEA labels should be recorded and repaired in time. The inspection log, including the inspection results and any corrective measures taken, should be kept there for inspection by the construction department and the fire department. The inspection log shall indicate the date of the inspection and the name and signature of the person performing the inspection.