The good price and quality emergency light rechargeable common wiring method
During the after-sales process of good price and quality emergency light rechargeable, it was found that emergency light rechargeable could not be used normally due to wiring errors. Moreover, this phenomenon is also common in price. Next, I will explain to you the common wiring method of emergency light rechargeable.
Emergency light rechargeable should be equipped with a dedicated circuit, and no switch should be installed in the middle. Two-wire and three-wire emergency light rechargeable can be unified on the dedicated power supply. The setting of each dedicated power supply should be combined with the corresponding fire protection regulations. If the emergency light rechargeable power supply is rotated separately from the lamp, the electrical connection of the automatic emergency light shall be high temperature resistant wires to meet the fire protection requirements.
This connection is a commonly used connection for A-type emergency light rechargeable, which is suitable for use in situations where the emergency light does not need to be used for lighting in daily life or when it is continuously illuminated for 24 hours. After the power is off, the emergency light will automatically light up.
Emergency light rechargeable wiring three-wire connection method:
1. The characteristics of various wiring methods must be accurately mastered, so as to avoid blind wiring and fail to play its due role;
2. If emergency light rechargeable is used as part of usual lighting, three-wire controllable connection should be used.
3. For projects with fire control management areas, in order to meet the requirements of fire control and fire emergency lighting on fire floor and related floors when a fire occurs.
4. For multi-storey public buildings, if there is no anti-control area, the emergency lighting fixtures in each part can be controlled by adding local switches (single lamp single control or multi-lamp control) or centralized control in the distribution box three-wire connection method .
Emergency light rechargeable two-wire system:
The connection method is a commonly used emergency light rechargeable connection method, which can control the on or off of the usual lighting state of emergency lamps. When the power grid is cut off, no matter what state the switch is in, the emergency light rechargeable immediately lights up the emergency.